Select Page: 1
Control.com member...Member Information and Posts by MS_5001
from the Control department...FSR Control
FSR control changing during base load
Dear CSA, >What is the frequency doing when FSR is toggling between Acceleration > and...
from the department department...Auto Synchronization problem
synchroscope in HMI 180 degree different than the scope on GCPP panel
Hello, The different of 180 degree of synchroscope is solved by invert the wiring of bus...
from the Control department...MOOG G771K200 problem
servo valve pulsate during starting
Dear all, The problem is not solved yet. We connect the rubber hoses to each of fuel supply...
Hello, The unit is new installed and its the first time to to do false fire. the hydraulic...
from the Control department...Hydraulic Ratchet problem
Hydraulic ratchet didn't work properly from time to time
Hello, The problem is gone after we turn on the ventilation fan for (3-5 min) and turn it off...
Dear all, The sequence of cooldown is: cooldown time: 10 hours ventilation fan running...
Hello, The problem is solved by sequencing the ventilation fan running time during cooldown. ...
from the Control department...Rosemount Diff. Pressure transmitter problem
reading of the transmitter problem
from the CONTROL department...Magnetic speed pickup
Magnetic Speed Pickup Software Configuration
CSA, The unit is new and it is under commissioning. we make download of m6b file to all three...
from the CONTROL department...Alarm: Trip mult. activ. too long or too often
What is the cause of the Alarm Trip mult. activ. too long or too often?
from the Control department...Interface between Mark VI & Cimplicity HMI
how to make interface between Gas Turbine MS5001 Mark VI & Cimplicity HMI project (***.GEF) file
Hello, the problem is solved by downloading configuration & firmware (Mark VI I/O ) thank...
Hello, its a list of the Diagnostic alarms that I have: <R> SLOT 2 UCVX DIAGNOSTIC...
Hello MIKEVI; I am talking about new installed unit gas turbine frame 5 MarkVI and we did these...
from the Control department...Bleed Valve
Bleed Valves is not closing at 95%
Dear CSA , Yes it's the same logic that I have , >> about bleed valve close after stop...
Dear all, I checked the logic of bleed valve. the command of bleed valve L20CB1X depended on two...
Select Page: 1
The ancient Italian art of pizza folding.