from the Forum department...Communication Problem with Moscad RTU (8XXXXXX)
We are facing a problem while communicating with Motrola Moscad RTU CPU 300. It has modbus protocol and we are able to bring around 300 modbus registers using kepware opc server but there are some addresses like 8XXXXX which does not look to be modbus.
By Hassan Tariq on 10 December, 2013 - 9:09 pm -
Yes your assumption is correct. Moscad RTU is connnected with Omni Flow Computer and then we are...
By Mark on 10 December, 2013 - 1:01 pm -
I forgot to add that PeakHMI can access all the registers in the Omni flow computer and can publish...
By Mark on 10 December, 2013 - 12:19 pm -
Hello, While Omni flow computers can respond to standard MODBUS, for some of its register, it...
By Jack D on 10 December, 2013 - 10:30 am -
Hassan, I am not familiar with Omniflow computers, but I assume what you are saying is the...
By Harvard on 10 December, 2013 - 9:59 am -
Are you sure it is 8XXXXX and NOT 8XXXX? If it is 8XXXXX then you could target from 800001 to...
from the programming language department...Scripting visual basic in Factorylink
I having a lot of error with script in visual basic of Scada Factorylink V7.5 of siemens.
Hello, What FactoryLink version?...
By oriel on 27 November, 2013 - 3:46 pm -
Hola Gustavo, En buena hora tu respuesta!!! As forever, thanks a lot for your answer. Best...
By Gustavo A. Valero P. on 26 November, 2013 - 12:36 pm -
Hola de nuevo Oriel! Veo que sigues intentando domar a ese caballo salvaje y poderoso que es...
from the INSTRUMENTATION department...EEPROM DOWN LOADER
How to download LVDT feed backs to HMI via eprom?
There are instructions for using the EEPROM Downloader and the I/O Configurator in the Mark V...
from the WonderWare Upgrade Failures department...WonderWare Upgrade Issues
Upgraded PC. WonderWare updated from 7.1 to 2012 R2 (10.6).
You may need to upgrade to a Ethernet processor also....
You will want to use the DA Servers that come with Intouch/WonderWare. WW Tech support can help....
By Benoit on 9 December, 2013 - 9:41 am -
Are you still using "DDE" communciation method within Intouch Window Maker access points,...
>Background: > >. . . The PC has a PKTX card that communicates with a SLC-504 ? Still...
from the department of redundancy department...Interfacing with a GE Mark VI
What are the best practices in interfacing with a GE Mark VI?
Bob, most power plant site I have seen that are using GE gas turbines and an Ovation DCS are...
I was aware that the Mark VIe could be equipped with the ability to communicate via MODBUS without...
By Bob Larsen on 7 December, 2013 - 10:30 am -
We are installing a MarkVIe and will use EPM DCS to interface, building our own graphics and...
from the Thermal department...Connecting I/O cards between two PLCs
How to give the signal of one PLC to other PLC.
You Should use 230 VAC relay instead... DO of 2nd PLC will operate a relay whose contacts are...
from the Software smithery department...EIPNET anybody used it?
This looks good but no examples.
from the Engineering department...N1OPC Server and ICONICS Genisis64
Looking for some help in Iconics Genesis64 with N1OPC drivers
By Brian E Boothe on 3 December, 2013 - 9:40 am -
No, it's Johnson Controls N1OPC....
from the Software smithery department...Ethernet/IP via HMI Advanced
Using HMI Advanced to test my Ethernet/IP device.
from the INSTRUMENTATION AND CONTROLS department...ALARM SILENCE BUTTON NOT WORKING
Alarm silence button is not working
Without reading any documentation, perhaps the HORN_SILENCE_PCB is reacting to the fault and not...
from the computer sceince department...SCADA Software Language
What software language does SCADA use?
By James Ingraham on 25 November, 2013 - 12:06 pm -
SCADA encompasses a large number of providers and technologies. There is no one language that...
from the for PC DNP 3.0 serial simulations department...DNP 3.0 serial simulator?
Do you know if there is any simulator software for the DNP 3.0 protocol over a serial RS232 connection?
By Yesid Alfonso on 25 November, 2013 - 9:57 am -
Cambio de Link para la descarga del simulador gratis DNP3: ...
from the c&i department...Alternative to Foundation Fieldbus to read process signals
Alternative to Foundation Filedbus to read process signals for monitoring plant operations
By Jonas Berge on 23 November, 2013 - 8:21 am -
FOUNDATION fieldbus is a good way to go. Learn more about benefits of fieldbus here: ...
from the Maintenance/Services department...WINCC software training
Looking for WINCC V6.2 training software Download
from the Forum department...Lock Graphic focus in FactoryLink
Need to lock the focus of graphic in FactoryLink
Hello, FactoryLink version? Graphic editor - old ECS or ClientBuilder?...
from the APCAM department...Comparison of various SCADA packages!!!
Can anybody explain me the features of various SCADA packages available in industries?
By nishant on 20 November, 2013 - 8:33 am -
Actually i am using astra and it works fine. i am using it with eurotherm controllers over modbus...
from the hrsg & gtg department...Gas Turbine Shut Down Signal
changing the signal trip of HRSG Boiler from the shut down gas turbine signal to speed's gas turbine reach to 2850 rpm.
By abdi on 18 November, 2013 - 11:49 pm -
Hi, The maximum speed for gas turbine frame 9 mark v is 3000 rpm. In my company there is 8 GTG...
By otised on 18 November, 2013 - 2:18 pm -
abdi, You have not provided much information. I am assuming the gas turbine is a GE Frame 9...
from the Forum department...Mark-V and Proficy Historian
Communication between Historian and Mark-V Cimplicity 5.1
Dear Sdbarman, Try to contact this person, he will sure try to help you in your issue. ...
from the Control & Instrumentation department...Using CMS in MKVIe
What is the function of CMS (Configuration Management System Software)?
By Ch Amir Islam on 18 November, 2013 - 1:29 pm -
Dear Sir , Are you asking about CMS Software's help?...
Have you read the Help topic on CMS? What didn't you understand about CMS after reading the Help...
from the Designing in SCADA department...Need recovery from Wonderware Intouch window maker starting error
I am having some working troubles in wonderware intouch window viewer
from the Installation and Commissioning department...Frame 9E Lube Oil Tank
Frame 9E Lube oil Tank low level
Dear CSA thanks for ur reply. I have checked P&ID and there is no dimension for LO tank. I...
nayan.sharif, Is it not possible to physically measure the distance from the bottom of the L.O....
from the POWER department...Powering simple cycle GE 9e from local mark 6e panel
Simple cycle GE 9e only from local mark 6e panel
Dear CSA Many many thanks for your wonderful reply... yes we have a local HMI and from that one,...
nayan.sharif, The real problem is: Why ISN'T the Control Room ready?! Why...
from the Forum department...TCP Smart Touch Cable pinout
Looking for support for an old TCP Smart Touch HMI
from the Business School Project department...Grad school project - take a survey and win a Rasberry PI
Help me with my term project and take an HMI marketing survey.
Cool Survey. I just filled it out.. I would loveee to win a Raspberry PI, I think those are so...
Mark's Dental-Chair Discovery:
Dentists are incapable of asking questions that require a
simple yes or no answer.