from the Engineering department...RS485 multidrop network drops after few days
Modbus connections drops after few days and it resumes by changing modbus parameters in slave device.
By Lynn August Linse on 3 July, 2014 - 1:21 pm -
Based on 25 years experience with RS-485, sounds to me like you have a floating ground between the...
from the electrical, domotics department...modbus-scada
is it possible in a modbus network to have a SCADA system which polls for data from the slaves and another SCADA system which also collects data from the same slaves?
By pvbrowser on 3 July, 2014 - 2:49 am -
If you use a Modbus TCP gateway in front of the Modbus RTU line it is possible. If you can only...
By Darrin Hansen on 2 July, 2014 - 10:57 am -
You can't do it on the same subnet, as a Modbus subnet can have only one master. But the ICC...
from the GFCI help... department...GFCI
I would like to install a GFCI in a control cabinet for a CNC machine.
from the Automation department...Multiple monitor one mouse
Operator has 2 computers each driving 4 monitors for a total of 8 monitors. Operator wants one mouse/keyboard for all 8. Anyone use "mouse without borders?"
By gman on 2 July, 2014 - 9:09 am -
Hi there search for software called synergy. I have used it to move between multiple pc's and...
Old Guy, Seems my first post didn't get "picked up"--the one where I mistakenly...
KVM stands for Keyboard-Video-Mouse (not Monitor)....
from the Automation List department...Re: Wonderware windowviewer issue
Wonderware windowviewer issue
from the HMI department...Wonderware windowviewer issue
Windowviewer only shows top.
Daniel, any chance you have one or more windows marked as "replace"? jack...
Hi !!! Thanks for the answer! I had already configured some home windows to be shown as you...
Hi Daniel, It appears that you haven't assigned any HOME windows yet on your project. Open...
from the Forum department...OPC interfacing for Infi90
By Paul on 26 June, 2014 - 2:12 pm -
>Is there any way to get raw (bypass the >exception report) process data from the ...
from the Stuck department...S7-200 connection to Citect
I'm failing to connect an S7-200 PLC to Citect, despite following Citect Documentation.
By sameer on 26 June, 2014 - 5:43 am -
i m trying to connect s7-200(224) to an existing citect scada. already 1 plc is connected to...
from the instrumentation department...mark 5 control system
Inlet guide vane stroke checking using demand display.
shyam, Simply because AutoCalibrate is not configured is not a reason to use the Demand Displays...
In our frame-5 machine auto calibration not configured, that's why have to use demand display. so...
By curiousone on 23 June, 2014 - 10:33 pm -
If AutoCal is not properly configured, and the stops on the valve not properly set. AutoCal can...
shyam, or SHYAM, I would highly recommend that you NOT use the Demand Display for stroking the...
from the controller department...MCC 400 breaker
MCC breaker opened
khairi, Again, without being able to see the one-line diagram for the turbine/plant, it's almost...
By KHAIRI on 20 June, 2014 - 9:50 am -
thanx for feed back its supply breaker for mcc and it happened with us when the turbine working...
khairi, "MCC 400 breaker" is not a description that many of us are familiar with. MCC...
from the Turbin department...ground earth
By KHAIRI on 20 June, 2014 - 10:07 am -
thanx csa for helping and i hope to learn from you more (you are my teacher)...
Hello, KHAIRI, or khairi, I don't think you can see or monitor the earth (ground) resistance...
from the URGENT SUPPORT REQUIRED department...Wonderware Communication Issue
Wonderware server application slows down on pulling out LAN wire or disable any of the four networks we use
By Jay on 18 June, 2014 - 6:37 pm -
For communicating with modbus over Ethernet, the DASMBTCP service works quite well with Wonderware....
from the Automation department...HMI in Class 1 Div 2 area
Can I use an intrinsically safe barrier or isolator to power a 24VDC HMI, rated for Class 1 Div 2?
from the DCS department...PLC Slow ethernet communication response
PLC Controllogix 5000 slow ethernet response
By Nick on 9 June, 2014 - 4:21 pm -
I too am having this issue! Compactlogix 1769 l35e and wonderware intouch software. We replaced a...
from the Instruments department...Conductor VMS dual monitors
having trouble to set up 2 monitors in a Digital (that's the brand) PC with Conductor VMS O.S. and SRM Bios.
from the Gas turbine Mark-vie PCAA Module department...4 or more bad Exhaust T/C fault
Gas turbine Frame-V got tripped on PCAA Module fault in MARK-Vie
vimal gupta, It would seem there are some new Diagnostic and Process Alarms since I've looked at...
from the Forum department...Instrument Tech Training Topics
My boss has asked me to create a training program from the instrument techs that is one 3 hour course a month for 2 years.
Providing a list of suggested topics to your intended audience is a great technique to spur a...
from the Simulation department...Automatic Volage Regulation
Question on the behavior of AVR after synchronization.
By engr on 29 May, 2014 - 8:43 pm -
We have on load tap changer for transformer. When generator MVARS are high (lagging side) due to...
By zahid on 23 May, 2014 - 11:03 pm -
My question is that if AVR is shifted from Auto mode to manual mode due to some transient with gen...
from the Forum department...Connection FCS DCS Yokogawa
FCS connection Centum CS 3000 Yokogawa
Please ensure tags are either global or transferred from one FCS to another with data link transfer....
from the Wish I knew department...Mark VIe 88BD motor HMI control Lead/Lag
Cannot control 88BD diffuser blower motors from control room HMIs
Norm, Is this one of those Mark VIe upgrades of a Mark V that came with new and/or upgraded...
from the ABB Advant department...ABB OS500 upgrade
ABB OS500 upgrade to newer version HP B2600
By Salvador Banos on 21 May, 2014 - 6:11 pm -
Hi, I'm not sure if you'd be interested, but I have developed an HMI system using an OPC Server...
By Bob on 20 May, 2014 - 8:28 am -
Will, This sure sounds like a power plant installation, perhaps with a Alstom trane, running a...
By Tony R. Gunderman on 16 May, 2014 - 4:51 pm -
Will, One potential method to create a hard drive image on another spare drive for quick...
from the Oil and Gas department...RTD failure
Unit trips at RTD failure when spikes occur
Re RTD failure: I had experience the same issue but the only difference is that we made changes...
from the Forum department...Conductor NT and Windows 7
Will Conductor NT install and run on a Windows 7 machine?
So, we did get it installed inside the Microsoft "XP Mode" virtual machine, and it does...
"Those who do not do politics will be done in by politics."
-- French Proverb