from the Automation department...HMI in Class 1 Div 2 area
Can I use an intrinsically safe barrier or isolator to power a 24VDC HMI, rated for Class 1 Div 2?
from the DCS department...PLC Slow ethernet communication response
PLC Controllogix 5000 slow ethernet response
By Nick on 9 June, 2014 - 4:21 pm -
I too am having this issue! Compactlogix 1769 l35e and wonderware intouch software. We replaced a...
from the Instruments department...Conductor VMS dual monitors
having trouble to set up 2 monitors in a Digital (that's the brand) PC with Conductor VMS O.S. and SRM Bios.
from the Gas turbine Mark-vie PCAA Module department...4 or more bad Exhaust T/C fault
Gas turbine Frame-V got tripped on PCAA Module fault in MARK-Vie
vimal gupta, It would seem there are some new Diagnostic and Process Alarms since I've looked at...
from the Forum department...Instrument Tech Training Topics
My boss has asked me to create a training program from the instrument techs that is one 3 hour course a month for 2 years.
Providing a list of suggested topics to your intended audience is a great technique to spur a...
from the Simulation department...Automatic Volage Regulation
Question on the behavior of AVR after synchronization.
By engr on 29 May, 2014 - 8:43 pm -
We have on load tap changer for transformer. When generator MVARS are high (lagging side) due to...
By zahid on 23 May, 2014 - 11:03 pm -
My question is that if AVR is shifted from Auto mode to manual mode due to some transient with gen...
from the Forum department...Connection FCS DCS Yokogawa
FCS connection Centum CS 3000 Yokogawa
Please ensure tags are either global or transferred from one FCS to another with data link transfer....
from the Wish I knew department...Mark VIe 88BD motor HMI control Lead/Lag
Cannot control 88BD diffuser blower motors from control room HMIs
Norm, Is this one of those Mark VIe upgrades of a Mark V that came with new and/or upgraded...
from the ABB Advant department...ABB OS500 upgrade
ABB OS500 upgrade to newer version HP B2600
By Salvador Banos on 21 May, 2014 - 6:11 pm -
Hi, I'm not sure if you'd be interested, but I have developed an HMI system using an OPC Server...
By Bob on 20 May, 2014 - 8:28 am -
Will, This sure sounds like a power plant installation, perhaps with a Alstom trane, running a...
By Tony R. Gunderman on 16 May, 2014 - 4:51 pm -
Will, One potential method to create a hard drive image on another spare drive for quick...
By Bob on 12 May, 2014 - 9:55 pm -
Most everything you have read in these posts is true. B2600 is becoming difficult to locate. We...
By jesse on 3 May, 2014 - 11:10 am -
I'm late to the party here.. the best controller that will work with the PU513 EISA are the B180...
from the Oil and Gas department...RTD failure
Unit trips at RTD failure when spikes occur
Re RTD failure: I had experience the same issue but the only difference is that we made changes...
from the Forum department...Conductor NT and Windows 7
Will Conductor NT install and run on a Windows 7 machine?
So, we did get it installed inside the Microsoft "XP Mode" virtual machine, and it does...
from the Forum department...White thick smoke from gt during start up and shutdown
white thick smoke coming from exhaust during start-up and shutdown.
Am a Frame 9E gas turbine control room operator. So i can categorically tell you that you can...
Nice contribution and comment.....
I had almost the same issue but it was duel fuel and it was happen only when operating on liquid...
from the Instrumentation department...RTD
RTD resistance value same but Different at HMI
try to check the value in the software. check the wiring and both MTL Barrier. try to simulate...
from the Private department...OPC Server and Excel
PeakHMI server installed
By Mark on 10 May, 2014 - 6:06 pm -
Hi, Since you bring up a post that is three years old I will add more. Since my original...
You can use www.rbsreport.com > I hope any one use the peakHMI server and client. > I...
from the E&I department...Freezing of AB PanelView Plus
Allen Bradley Panelview Plus HMI freezes with a pop-up error message.
By Bob Peterson on 10 May, 2014 - 11:47 am -
take a look at knowledge base articles 44733 and 470512. -- Bob http://ilbob.blogspot.com/...
from the Any advice department...Option to run AC lube oil in manual YES OR NO
Should we have the option to run in local?
Craig, Every site is not the same. It all depends on what was bought, what was sold, and what...
By Dave Amundson on 9 May, 2014 - 9:42 am -
I can't comment on your switchgear options to run the AC lube oil pump, but bearing lube oil feed...
from the Forum department...Need help scaling Tridium Niagara AX front end with Modbus TCP points
I have a Wonderware Intouch front end with Modbus TCP points that I am replacing with Tridium Niagara AX.
from the High department...Honeywell connection an output Scada point to a PID Block?
how connect an output Scada point to OP PID Block in control module?
from the Urgent department...Calling up filtered alarm list
Creating a filtered alarm list in Honeywell HMI station
from the Forum department...upgrade MARKV hmi to windows2000
Mark V HMI Upgrade
By curiousone on 30 April, 2014 - 10:03 pm -
Old question! Upgrading from NT 4 to Win 2000 helps tremendously. Win 2000 has device manager that...
By Pioneer on 29 April, 2014 - 8:40 am -
hi dear expert. please explain how you did this? Thank you. > ok. our hmi upgraded to...
from the Urgent department...Call up group trend in Honeywell Station
When calling up a group trend in Honeywell station pushbutton in HMI it does not go to correct group.
Thank you so much. It works. Can I do this for alarm list? They want me to put a pushbutton...
By giker_86 on 29 April, 2014 - 7:58 am -
If You have an Experion system you need to do following steps: 1. Add a new Button to display. ...
from the HMI Upgrade department...ABB / Bailey Conductor NT
Upgrading from Conductor NT 6.0 to Symphony Plus?
By John on 29 April, 2014 - 6:00 am -
I'm hearing that they have a SODG graphic conversion tool that is VERY clean. I think that the tool...
from the how to change the Engineering units department...OSI PI Engineering units conversion in GE Control System
Stuck with the US engineering units
By Rob on 29 April, 2014 - 2:51 am -
In Process Book? - You don't. Modify the tags in the PI server using the Bulk Excel tools. Since...
from the Normal department...Honeywell scrip language
How can we learn Honeywell Scrip language?
Search support at http://www.honeywellprocess.com Or if you have training budget you can find a...
from the IT department...Modicon M340 TCP Communication
Communication between Modicon M340 PLC and Weintek HMI via MODBUS TCP
from the Forum department...How to connect Magelis XBTGT6330 to Modbus Plus Network
Is there need for accessories like modules or adapters to connect the Magelis XBTGT6330 HMI to Modbus Plus network or it can be connected directly to the Modbus Plus network without using extra hardware?
By DH on 23 April, 2014 - 10:52 am -
Do you know what driver was used for Vijeo Designer for the Magelis to work with the Anybus-gateway...
from the Forum department...How To connect Vijeo citect with Untiy Pro XL
help me to connect Vijeo citect and unity pro xl
from the Automation List department...Android tablet for HMI?
Using an Android tablet as an all in one PLC.
By Peter Fredriksson on 22 April, 2014 - 4:32 pm -
Hello, I hope you all will not see my post as a advertisement. We are a small family company...
from the PSEB department...TDC 3000
How to print tag nos. and descriptions of historised points in TDC 3000
By Tim Haywood on 22 April, 2014 - 6:05 am -
Hi - anyone who is looking for similar information may find these information books very useful -...
"The two most common things in the universe are hydrogen and
Control.com is the largest Automation community on the web. Learn how to advertise here now...