APS 5000/TDC 3000 History Module Replacement
History module bad sector encountered on Yamatake APS5000/TDC3000 DCS and needs replacement.
Transmitters Calibration Interval
What is the recommended interval for calibration of transmitters, DP, temperature, and pressure transmitters.
By rsaradhi on 1 March, 2015 - 2:06 am
Hi, 11.3.2 The accuracy of all electronic liquid measurement (ELM) equipment should be verified...
By rsaradhi on 1 March, 2015 - 1:45 am
Hi, > Is that calibration interval recommendation in the 2013 version/edition? Please note...
GE 9FA Gas Turbine - Fuel Changeover Load
GE 9FA Gas Turbine Changeover Load
Level Control for Water Tank
What kind of level sensors to be used to control the water level in a tank provided there will be level sensors to monitor 3 specific points in the tank.
Antisurge Algorithm for Centrifugal Compressor
Antisurge control for centrifugal compressor with variable speed: Algorithm implementation in Unit Control Panel
VTScada 11 hmi software? Any thoughts
Looking for feedback on anyone who has integrated systems using this software.
By Gettingitrightthefirsttime on 27 February, 2015 - 3:39 pm
I've been using various HMI software products for over 20 years, including VTScada, RSView, WinCC,...
Measure the oil level in a tank over a range of temperatures
By Roy Matson on 26 February, 2015 - 4:41 pm
Ron, I agree the pressure will remain constant regardless of temperature. However it will...
Convert Flow Rate from kg/hr to litr/hr
How do I can convert flow rate from kg/hr to litr/hr?
By Roy Matson on 26 February, 2015 - 5:21 pm
You have realized that compressible fluids are far different from non-compressible liquids. Really...
By otised on 22 February, 2015 - 1:00 pm
Assuming you intend to test this flow meter in a line passing oil with a density of 794 kg/cubic...
Can't install software without floppy drive.
By shoaib on 24 February, 2015 - 9:13 pm
Dear expert how i can generate a key code floppy disk files from an existing HIS? My key code...
OPC Tunneling Inter vendors
Is it possible to communicate MatrikonOPC Tunneler with Kepware OPC Connectivity Suite?
Looking for Information about OPC Servers
When do we need to use OPC SERVER?
Separate Instrument Earth Pit
Separate Instrument Earth pit not available
Remote Set Point Temperature Controller
Looking for recommendations for a remote set point PID controller
Turndown Ratio of Dual DP Cell on Orifice Stream
Need help calculating the turndown ratio of dual dp cells on an orifice system.
Rosemount GWR Length Reduction Creating Measurement Errors
I have adjusted the Rosemount GWR lenght but the level measurement is now inaccurate.
Comparing Temperature Transmitter Models
Model Number comparison between transmitter giants
Micrologix1100 To Citecscada6.10
Communication Between Schneider Electrics CitecSCADA6.10 Service Pack A and AB Micrologix1100 via EtherNET/IP
I want to know what OS is required to be installed in Magelis HMI GTO and what about runtime license required?
By Brian Cervi on 19 February, 2015 - 7:36 am
I am noy sure, but the version may show on the screen when the HMI first powers up. VJD software...
By Brian Cervi on 16 February, 2015 - 3:21 pm
I must appologize for all the grammar mistakes in my reply. I wrote it on my iPAD from a chair by...
By brian cervi on 15 February, 2015 - 11:16 am
The GTO lmodels are programmed using Vijeo Designer software, which installs on Windows XP thru 7....
Looking for a Pressure Transmitter operating Range 0-600 Degree Celsius for 15" WG line
Pressure Transmitter required for operating Range 0-600 Degree Celsius for 15" WG
Time Synchronization with SCADA and MODBUS
This is regarding the Time Sync term required for SCADA to configure the MODBUS device.
Mark V: S Core Re-booted Several Times
On Mark V TMR system S core rebooted several times and found stuck in A6 status. When S core rebooted manually it successfully attained A7 status.
Magnetic pickup - amplitude or frequency
Magnetic pickup - amplitude or frequency
Simple Ladder Logic Question
Programming a conveyor motor. I seem to be stumped at the moment.
DCS Analog input signals didn't work with ADAM card